This is the importance of carrying out annual boiler servicing. Catching issues early and preventing ongoing and potentially dangerous issues from arising. I attended to
Attended to a property where the flush drop valve was letting by. This was replaced with new. Tested for correct operation, tested and left working.
No job too small. Removal of existing lever handled flush and replaced with new.
Annual boiler service carried out. If we can be of help. Call or WhatsApp us on 07918-733-040 Previous Next
Attended to a property where reports of the sinks were not draining. Found the external waste blocked. This was cleared and both sinks were left
Landlords gas safety record completed prior to a change of tenancy
Removal of existing bathroom/ shower suite and replacement of new. Aqua panelling throughout, new shower and suite along with tiled floor and towel rail Previous
Replacement of kitchen taps for new
Installation of a new ideal boiler complete with 5 years parts and labour warranty. The precious boiler was beyond economical repair due to multiple issues.